Engineering & Specifications
Deringer 20 Double Check (DC) valve shall utilize two independent Dual Action Check modules and two integral resiliently seated shut-off valves
all of which shall be contained within a single rigid valve housing constructed entirely of 304 stainless steel. Both integral shutoff valves shall include pre-wired
supervisory tamper switches contained within a weatherproof actuator housing approved for both indoor and outdoor use. Dual Action Check modules shall operate as a
“poppet style” check under low flow conditions, operate as a “swing style” check under high flow conditions and utilize replaceable silicone elastomer sealing discs.
Assembly test cocks shall be handle-less and operate via a tamper resistant actuator. Assembly shall have a single full access service port and cover with an “inline”
replaceable elastomer seal. Assembly shall be serviceable without special tools and approved for both horizontal and vertical applications.